We will be Close From midday on Thhrsday the 21st of December to the 2nd
Electrical Safety | Parker's Electrical NQ
THE EARTHING SYSTEM
The most important part of you electrical system is the earthing system as this is what helps protect you and your family from
electrical shock. The earthing system connects all your appliance with conductive parts (ie. stove, washing machine, fridge...) so that if there
was an active fault in the appliance the circuit protection would trip and the appliance would not become live. There are many parts to the earthing
system from the earth electrode (pictured) outside your home to the connection on the appliance, some of these parts are inside the main
switchboard that includes a connection to the main natural as well as other places. Your main earth electrode should not be a piece of pipe it should be
a copper plated steal rod like the pitcher with a tag on it.
Are you experiencing electric shocks from metal parts in your home (ie. stove, fridge, water tap...)? This could be a sign that the neutral
connection has come to fault and potentially dangerous voltages are leaking back onto the earthing system (since the neutral and earth are connected).
Your lights could be flickering or your appliances behaving strangely as they are all receiving odd voltages.
Is your earth completely surrounded by concrete? This could potentially become a shock risk as the resistance of the earthing system to earth has
become of a high resistance. The current flows in the path of least resistance. This means that the earthing electrode has a resist so high that
it no longer operates as it is designed to and the current does not pass to earth. Have you had work done on your home like external walls being
re-sheeted ? if so check your earth has not been disconnected as we have seen this to be the case on some jobs.
The next part of yourelectrical
safetyis the circuit protection device (ie. circuit breaker of fuse). If your home still has
fuses (pictured) we recommend replacing them with circuit breakers and/or circuit breaker RCD combination protection as fuses is technology that is
over a century old and at least 30 years out of date. This is where we find most power faults in older installations.
Plug in Circuit breakers are not an acceptable replacement solution as, like fuses, anyone can put any size breaker in and overload the circuit which in
turn can cause fire. For example a large 32A circuit breaker (stove size) into a 6A wiring situation (lighting circuit).
This type of protection should be replaced immediately as it is out of date and can be dangerous.
To the left is circuit breakers that are used today (varying in appearance based on brand). But wait, that's not all. After the fuse was removed
circuit breaker protection was installed to improve electrical safety. Some years later it became law that your power AND LIGHTING circuits have to be
protected by RCD (Residual-Current Devices).
I can not say enough about the need to replace the old fuses with residual-current circuit breaker (rccb) as these new devices are real
life savers and the old fuses are very bad protection against electrical shook, and i wood say that 50% of the faults i deal with are related to
fuses, normally in the way of the wire burning off the back of them.
The next is the Residual-Current Device (RCD) that is probably the most important thing you can have put on your homes electrical system. In fact,
in Australia, it is law to have an RCD on all your power and lighting circuits, this includes 3 phase outlets.
You can test these with the test Button on the device, but we recommend that if you have just bought your home that you have a qualified electrician to
test the operating of an RCD with a proper Residual-Current Device tester. The test Button only tells you that they will trip but not if they are doing
their job in the required tripping time.
Lastly, in years gone past many electrician install one RCD to protect the entire building. We recommend against this and it is frowned upon today
because if you have a fault on 1 circuit you could lose supply to your whole home. Instead we use residual-current circuit breaker (RCCB) on each
circuit, this device is a Residual-Current Device and a circuit breaker in one.
POLL RCD 2
POLL RCD RCCB
ISOLATION LINK / MAINS PROTECTION
All switchboard should have mains protection and any new switchboard or switchboard that have had metering work modifications must have mains
protection. The most common form of mains protection is a CB on the penal near the meters that is sealed by Ergon and has a sticker(
contact an electrical contractor if this circuit breaker is in the tripped (0) position), the other way of doing this is to have a meter isolation
link and a CB as the main switch, this in most cases is not recommended as there will be more then 1 main switch and the rating on any one might be too
low and cause nuisance tripping.
Parker's Electrical NQrecommends
that everyone that has old fuses in thereswitchboard
inquire about a upgrade immediatelyas
they are over 30 years out of date and can be a fire danger. We recommend
that you have all your power and lighting circuits on a residual-current
circuit breaker (RCCB), have mains protection, and you have the whole
installation checked every 2 years and as soon as possible after a cyclone
when your house has had any damage.
The reason for this recommendation is that RCD's can go faulty, earths can
break, neutrals can also break off at the pole or mains box. The
electrician should check you're earthing system including fans and lights,
your active and neutral connections, all the connections in the switchboard,
a RCD test with results, and a fault loop impedance test. The resulting
tests should then be supplied to you in the format of a report with required
changes and recommendations that has been found.
This article is the opinion of Parker's
Electrical NQand is only a guideline, for more information contact your Electrical Contractor.
Parker's Electrical NQ is introducing the new Clipsal Iconic range.
Clipsal Iconic is a modern electrical accessories range, based on a slim, sleek, clean design that is easy to
blends in with your environment.
The Iconic range is loaded with clever features and benefits like new game changing modular mechs and grids with changeable skins and
dollies for unrivalled customization now and in the future. Clipsal Iconic – next generation wall switches and sockets that give you more
options than ever before and makes it easy for our costumers to change the look
of there switches when they repaint.. Parker's Electrical NQ is one of the first in
Townsville to use this range in a new House.
HAVE YOU RECIEVED A ERGON DEFECT? These defect
can be about the connection to your property or a switchboard
fault. If so then give the professionals a call, Parker's Electrical
NQ can correct the defect at a very reasonable price, and our
electricians can advise you on any other issues you my have, it is
always a good idea to have you're switchboard and mains checked by a
Electrical Contractor every few years as things can become
overloaded or damaged and out of date.
Monday to Friday 7:00am to 5:00pm 24 Hour
Emergency call out service 7 days a week.
43 Canara St Cranbrook QLD 4814 Australia
You can also see us on
NEED A QUOTE
We're happy to provide a free, no obligation quote on any
electrical work you require. Get in touch with us via our contact form, provide
us with some details and we'll get back to you promptly to discuss youre needs.
You can also call on 0488571866
You are page visitor No
and site visitor No 15471 hits